b. Article – combustion chamber:
– Deal with all the gas has a minimum temperature level of 1100 ° C using a minimum residence time of two secs the afterburner is to; – An extra air injection is expected as well as gives best oxygen material; – The heater makes sure a minimum temperature of 1100 ° C continuous; – The design of the heater resembles burning burners; – The afterburner is– equipped with accessibility doors to be able to ensure normal cleaning– of dust; – The afterburner is lined with high thermal insulation with a thickness of 150 millimeter
c. Closet, controller along with regulation: – The whole installment will accommodate European standards( EU ). – The electric power is 220V 50Hz solitary phase. – Regulatory authorities of temperature with electronic display screen:.
Follower power 0.37 kW
– – The cellular lining is made of refractory blocks and also a thermal insulation making certain a minimum temperature of this sheet;
? Permit limited gas intake
The incinerator with pyrolytic combustion should have:
– – Chamber solid steel support legs sheet;
CAPACITY OF INCINERATION 30KG/ H
1. BASIC SPECS:
The incinerator for clinical waste ought to be assigned for the harm of all sorts of waste produced by the Facility for Wellness (waste type medical centre, facility, medical laboratory for devastating capability of 30kg/ h).
Pyrolytic gasification combustion control shall:
? Prevent development of black smoke and also dust development tine loading of waste;
. PRODUCT MEASUREMENTS
Summary Dimensions. Destructive ability 30 Kg/ hr. Procedure 12h/24, 6d/ 7. Smokeshaft Elevation: 5m, Diameter: 280mm.
–? 1 to handle the temperature of the burning chamber. ? 1 to regulating the temperature of the afterburner.
Amount of combustion
chamber Burning: 0.3 m3.
– – The sole burning Is Composed of a refractory lining particularly created to meet the thermal, mechanical and corrosive liquid waste requirements and liquified glass;
? Provide regulated guaranteeing the absence of shade, cloud of smoke or shedding odor;
– – Running temperature: 1650 ° C max
? The hands-on controls are provided on each item
– – Nature: Calcium Silicate
– – The restoration operation of the ash will occur once a day line prior to beginning the day’s process.
– – The dimensions of the floor are geared up laterally primary air nozzles that maintain combustion;
Blog article burning: 0.2 m3. Combined burning chamber: 0.3 m3.
– – Nature: Refractory bricks with 42 alumina – Density: 110mm
– The combustion chamber is geared up using a burner to line to ensure right temperature level for the overall damage of waste combustion; – Automatic monobloc burner and flame dive furnished with an electronic ignition system along with permanent air flow. Air fan: – A most important air and secondary air follower gives the required oxygen delivery – There is an electric motor controlled shutoff that regulates the flow based on the combustion. – The strain of the follower is 500 mm CE to pierce the mass of
– – The fireplace is outfitted with a mixing system of waste burning is regulated switch;
– – Operating temperature level: 1000 ° C max
Follower power 0.37 kW